MTS Power Products serving all of South Florida for over thirty years for their industrial and commercial generator needs. If your Genset needs an Automatic Voltage Regulator for Generator, give us a call. Generator Automatic Transfer Switches, Generator Governors, Generator ATS Controls, Generator Battery Chargers, Generator Engine Controls, Generator Auxiliary Excitation Booster and many other Generator accessories. We can customize any aspect of a Genset to your exact specifications with our custom machining shop, welding shop, electrical department and mechanical engineering department.
An AVR or automatic voltage regulator for generator is used for delivering power to the electrical fields for both brushless and commutator style exciters and will maintain the proper voltage for an AC (alternating current) generator, a one percent plus or minus of the exact preset value with paralleling.
An automatic voltage regulator for generator is best used when a generator load alters between having zero load and a rated load with a frequency change that is greater than plus or minus four percent. When the application occurs or a rejection of rated load, a generator’s voltage will recover to a plus or minus one percent within 0.3 of a second on most automatic voltage regulator for generator exciters for AC (alternating current) combo.
An automatic voltage regulator for generator operates best when the ambient temperature hovers around 50 degree celsius. This creates an electrical power output of 150 W (watts) with a maximum current of 3 Amp (amperes). Each generator manufacturer operates with varying circumstance causing the AC (alternating current) generator wave length shape changes are noticeable from zero load to a rated load.
This is mainly due to the exact type of load, thus the rms (root mean square) will maintain average or peak voltage does not stay in proportion. When this occurs, for example, more than a ten percent harmonic distortion, for the voltage regulation may be outside the actual limit that is specified.
How does the automatic voltage regulator for generator operate? If a rated load is switched on to an AC (alternating current) generator the voltage will fall to around seventy percent of the no load value. The AC (alternating current) generator voltage should be maintained closer to the no load value. The excitation must incur with a gradual increase proportionally to the amount of the load or more appropriately in proportion to the exact fall in voltage. This is the basic function of an automatic voltage regulator for generator.
Call MTS Power Products if you have any question about an automatic voltage regulator for generator. 305-634-1511